Why do I get wrong values when reading a PCD2/3.W340 with media mapping?
PCD2.M5xx0 and the PCD3.Mxxx0 systems equipped with firmware 1.10.16 did not correctly calculate the temperature values of NI1000 temperature sensors measured with PCD2/3.W340 input modules.
The temperature read by the media mapping for Ni1000 sensors which are connected to a PCD2.W340 or a PCD3.W340 installed on a PCD3 or a PCD2.M5 is not correct with firmware version 1.10.16.
The firmware did not correctly convert the measured signals to the according temperature.
Please update the firmware of your PCD to version 1.10.51 or later.
PCD2 / Wxxx
PCD3 / Wxxx
PG5 2.0 / Device Configurator
Last update: 31.05.2015 14:51
First release: 06.05.2010 18:56