Saia PCD Supervisor
Information about the Saia PCD Supervisor
SBC’s scalable software platform Saia PCD Supervisor monitors and controls simple HVAC controls as well as enterprise-wide control stations of major building complexes or infrastructure installations. Open communication standards enable the integration of external systems. The easy handling of Saia PCD devices ensures efficient system management, as well as a high operating comfort through the customizable user interface, dedicated dashboards and a remote Function.
Saia PCD Supervisor is based on the Niagara 4.4 update 1 platform from Tridium.
This software core has been used successfully worldwide for many years. Compared to the standard version of Tridium, our Saia PCD Supervisor includes, among other advanced BACnet Utilities, an Ether-S-Bus driver, the PG5 Icon Gallery and a PG5 Data Import Wizard for easy and fast integration of Saia PCD controllers.
Saia PCD Supervisor Documents
Saia PCD® Supervisor
|Flyer||PP31-061||Saia PCD® Supervisor|
Saia PCD® Supervisor EM
|Datasheet||PP34-002||Saia PCD® Supervisor EM|
System Catalogue : Saia PCD Supervisor
|Extract||PP26-215_B0121||System Catalogue : Saia PCD Supervisor|
Saia PCD® Supervisor
|Datasheet||PP34-001||Saia PCD® Supervisor|
Saia PCD® Supervisor is a building monitoring and management solution built upon the powerful Niagara 4 platform. It is capable of integrating Saia PCD® controllers, third party devices and internet protocols into a centralised software platform that is designed to manage buildings at an enterprise level.
Saia PCD® Supervisor
|Manual||27-651||Saia PCD® Supervisor|
Software package Saia PCD Supervisor
Demonstration project for the Saia PCD Supervisor
Saia PCD Supervisor demo web page
|Sales Support||Saia PCD Supervisor||Saia PCD Supervisor demo web page|
Demonstration page created with the Saia PCD Supervisor.
To display the application use the 'Google Chrome' web browser.
If other browser are used then not all features of the Saia PCD Supervisor will be avilable.
BACnet certificate for Saia PCD Supervisor
BACnet BTL certificates (by WSPCert)
BTL certificate: Saia PCD Supervisor
|Sales Support||BAC-BTL-30343||BTL certificate: Saia PCD Supervisor|
BTL certificate 30343 from BACnet International
Link to the BACnet certification of BACnet International (BIG-INT)
Software (except PG5) / Saia PCD Supervisor
Which operating systems and relational database servers are supported for Saia-PCD Supervisor installations? (FAQ #102025)
The Saia-PCD Supervisor runs on:
- Windows 10 (32-bit)
- Windows 10 (64-bit)
- Windows 8.1 Professional/Enterprise/Ultimate (32-bit)
- Windows 8.1 Professional/Enterprise/Ultimate (64-bit)
- Windows 7 Professional/Enterprise/Ultimate (32-bit)
- Windows 7 Professional/Enterprise/Ultimate (64-bit)
- Windows Server 2012 R2 Standard/Enterprise (SP2) (64-bit)
- MS SQL Server 2016
Detailed overview about the supported operating systems and relational database servers for Saia-PCD Supervisor installations can be loaded over the following link:
On the Niagara article, for the Saia-PCD Supervisor version 1, check the column with header line N4.3
On the Niagara article, for the Saia-PCD Supervisor version 1.1, check the column with header line N4.4
It’s possible to display the texts on the Saia PCD Supervisor in different languages? (FAQ #102019)
Yes it’s possible to display the texts for the operator of the Saia PCD Supervisor in English, German or French.
Please note, that only the texts for the operator will be displayed in German or French, but the texts for the developer will be still in English.
More information can be found on the support homepage of the Saia PCD Supervisor.
Why after the crash of the PC the platform daemon for the Saia PCD Supervisor doesn’t restart automatically? (FAQ #102012)
If the PC where Saia PCD Supervisor is running, was powered off without shutting down the Saia PCD Supervisor then it’s possible that after power on of the PC, the platform daemon used from Saia PCD Supervisor will not start automatically during system restart.
It’s necessary to start the platform daemon for the Saia PCD Supervisor manually.
The attempt to start the daemon via a batch script didn't work either.
A modification on the registry could solve the problem.
The problem is not in relation with the platform daemon used from the Saia PCD Supervisor but it’s a problem in relation of the Windows internal timings between window services.
To solve the problem, the following modifications on the registry entry of the concerned PC should be done.
Make the following steps:
In Windows, go to Start > Run > and type regedit
Navigate to: HKEY_LOCAL_MACHINE\SYSTEM\CurrentControlSet\Control
With the control folder selected, right click in the pane on the right and select new DWORD Value
Name the new DWORD: ServicesPipeTimeout
Right-click ServicesPipeTimeout, and then click Modify
Click Decimal, type '180000', and then click OK
Restart the computer
If this in insufficient, try setting to 300000