The requested software / document is no longer marketed by Saia-Burgess Controls AG and without technical support. It is an older software version which can be operated only on certain now no longer commercially available products.
Strange behaviour of digital modules PCD6.E100, PCD6.E610, PCD6.E611 or PCD6.A350 (FAQ #100264)
These 4 digital I/O cards have all an address range of 32. Therefore it is absolutely necessary to set the Base address to a multiple of 32. A Base address like e.g. 48 will cause problems.<?xml:namespace prefix = o ns = "urn:schemas-microsoft-com:office:office" />
What is the difference between a PCD6.A200 and a PCD6.A200 Z02 (FAQ #100633)
The PCD6.A200 Z02 is a special customer version for EPAL Portugal. The PCD6.A200 has a 24 V supply for the relays and the PCD6.A200 Z 02 has a 48 V supply for the relays. Otherwise the modules are identical.