How many web-clients can be connected at the same time to the S-Web Server over Ether-S-Bus?
The first generation of PCDs with integrated S-Web server did not support http-direct (e.g. the PCD1.M125, PCD1.M135, PCD2.M150, PCD2.M170, PCD2.M480) . Therefore the access of the S-Web Server must be realized using the free software "S-WebConnect" which is to be installed on a PC (accessing the PCD using e.g. Ether-S-Bus). Alternatively, an MB Panel can also access the S-Web Server (e.g. using Ether-S-Bus).
However, it is important to know that only one S-Bus client can access the S-Web Server over Ether-S-Bus at the same time!
By desing the S-Web Server of a PCD can only be accessed by one S-Bus connection per physical port (Serial-S-Bus, Profi-S-Bus, Ether-S-Bus). As result it is possible to access the S-Web Server over Serial-S-Bus and in parallel over Ether-S-Bus, but it is only possible to have one Ether-S-Bus Master which connects the S-Web Server.
That means it is not possible to access the S-Web Server of a PCD at the same time with the S-WebConnect (Ether-S-Bus) and the MB panel (Ether-S-Bus) because in this case the S-Web Server is accessed 2 times trough the same physical port (Ethernet Port).
Here you can use the Web Connect as frontentd. The S-WebConnect will serialize the web requests and therefore avoid two parallel connections.
- The WebConnect creates only 1 connection to the Eternet Port of the PCD (Ether-S-Bus to a PCD1.M135 for example)
--> there is no problem, because only one connection was created
- With the MB panel, instead to accessing the WebServer of the PCD directly (with the Ether-S-Bus protocol), the MP panel can be accessed indirectly via the S-WebConnect.
For this example the following configuration is to be done in the MB panel configuration:
- HTTP direct
- Remost host IP of the PC (where the WebConnect is installed)
- as html file to open, you have to write: WebConnect_Connection_Profil/File_Name.html (htm)
For more information please refer to the manual for the "Web Server Classic" (26/790).
PCD1 / M1x0/M1x5
Communication / Ether-S-Bus
Tips for SBC internals / http-direct
PCD7 / D4xx (MB Panel)
Last update: 29.05.2015 13:30
First release: 01.06.2010 14:34