The requested software / document is no longer marketed by Saia-Burgess Controls AG and without technical support. It is an older software version which can be operated only on certain now no longer commercially available products.
(replaced by PCD3.T665 | T666)
Ethernet RIOs Saia PCD3.T660
|Datasheet||PP26-500||Ethernet RIOs Saia PCD3.T660|
Smart RIOs PCD3.T660
|Manual||26-892||Smart RIOs PCD3.T660|
Software / Tools
For the power calculation of the I/O modules the Device Configurator from PG5 2.0. SP2 or later is to be used.
PG5 2.0 Device Configurator does also feature a label creator for the I/Os on the RIO.
Latest maintenance firmware version
PCD3.T660 | Latest maintenance firmware version 1.14.26
|Firmware||PCD3.T660 | Latest maintenance firmware version 1.14.26|
Good to know
The PCD3.T660 will be discontiued by the end of 2012. The repair service for the PCD3.T660 is guaranteed until end of 2014.
The PCD3.T660 Ethernet RIO has been replaced by the Smart Ethernet RIO PCD3.T665 or PCD3.T666. The T665|T666 are more performant than the T660, support the Ether-S-I/O communication protocol and can be programmed.
When replacing the PCD3.T660 Ethernet RIO with a PCD3.T665 or PCD3.T666, the user program of the Manager has to be adapted.
PCD3 / T660
How to configure the ethernet RIO PCD3.T660 without knowing its current IP address (FAQ #101290)
You can use SBC Webconnect to get access to the configuration webpage of a ethernet RIO.
If you don't know the IP address of the ethernet RIO in front of you you aren't able to get on its webpage and configure the desired IP address.
Start SBC Webconnect.
Start an internet browser and go to the address localhost. Following page will appear where you click on 'Add station':
Now enter the data exactly as shown below and click 'save':
Back in the main screen of webconnect you can see the newly created entry:
Hook up the RIO with a USB cable to the PC and click on 'usb'. The configuration webpage of the RIO will be shown.
Why doesn't the PCD3.T660 accept any configuration anymore? (FAQ #101289)
In case the Ethernet RIO stays in a state where it waits for its first configuration and the status LED remains red. IN this situatino the configuration webpage works, but the status LED stays red.
A total reset will bring it back to working condition.
The Ethernet RIO PCD3.T660 ignores configuration sent by a PCD and stays in a unusable state where its status LED stays red. The configuration webpage is working but not the download of the configuration with the "Send config"-FBox. Changing the IP doesn't help either. The device is stucked.
In order to re-use this device, please follow the procudure below:
- Power the Ethernet RIO off, then on again.
- Immediatly start pressing and holding the button just next to the Ethernet port. The status LED will begin to flash red.
- Keep holding the button until the LED starts flashing red/green/off (takes around 30 seconds).
- Release the button and wait some seconds until the flashing stops.
After this procedure all settings of the RIO are reset.
Now please re-configure the RIO via its configuration webpage again. See linked FAQ 101290 on how you can perform this task. After this new configuration the RIO will again accept the configuration sent by the PCD.
Why is the "diag"-LED of the PCD3.T660 illuminated? (FAQ #101260)
The "diag"-LED is always active and doesn't show any useful information (yet).